At this point I think it would be best to call you contractor. Temp sensor checked good. . If the pressure does not meet the switch setting, then you have a drain, venter,tubing issue. The gas ignition controller is a third-party supported product. What flash code are you getting? Contact Us at +1 844 628 2529 We can help you with a solution tailored to your specific needs. . Will Give it a shot first thing in the morning. . . . . The installer should pay particular attention to the words: NOTE, CAUTION, and WARNING. All units have two compressors with independent refrigeration circuits to provide 2 stages of cooling. . . Can you please help me. . Default fan OFF AND ON settings in the board are 30 SECOND ON and 60 SECONDS OFF. Thanks for your time. . ( Log Out / . Maybe they had a phase problem or power surge. . The unit was working when I arrived Friday afternoon. . . All pressure switches and freeze stat’s are closed and low AMB is open. . SKU: S1-031-03032-000. . . . . Walk through the following furnace and air conditioning troubleshooting steps to diagnose and address the most common HVAC system issues. FREE Shipping. . . . . I am a local distributor (Ukraine). User manuals, York Heat Pump Operating guides and Service manuals. . . . . thank you very much. My husband checked and at first there were two flashing lights. . . YORK® Predator® units are convertible single packages with a common footprint cabinet and common roof curb for all 3 through 12.5 ton models. . I turned the heat up and I was able to get a flame going. To make these flash codes more understandable in our commercial equipment — below is an explanation of each flash code. . . . You still need to make the diagnostic based of the flash code. I will check and keep you updated. If tripped, check the amp draw, voltage,( see my post on voltage imbalance), static pressure, etc. Go for Electric scheme of contact Limit look for 24V. Heating section showing normal heart beat led. M#ZF180N32J5AAA1B Thank you. I could not find anything wrong while I was there so I checked the last error codes. Pat, Sounds like you lost the limit input to the main board. it shows on the bord D18 HEAT DELAY ? . . . They said it had been cooling fine all day. ok i have a york unit with this board and i cant figure out what is going on with it. They are manual reset. split-system heat pumps There is 24volts at Y-out and Econ at the board. . . . Could be flame failure,open limit,cycling on limit,roll out switch etc. With a single stae stat, if in the econ mode there is no call for mechanical cooling if the econ cannot keep up. . We have a York M# ZF240N24AAA1B S# N1A0506845 That will not let C1 or C2 energize on the board. FC 10 – When flashing, it indicates the compressors are locked out because the low ambient switch is closed. On lockout 13 if I have a constant 24 volts at board on r and it’s passing 24 out to g and y2 why is it locking out y1.. Change ), You are commenting using your Twitter account. . Thu, Jan 21 – Thu, Jan 28 Arrives at 98837; YORK® Predator® units are convertible single packages with a common footprint cabinet and common roof curb for all 6-1/2 through 12-1/2 ton models. After reading the chat, I decided, you know the answer. Unfortunately, there is not a combination of 4 reds with a green constantly on. York Brand ZH120N20A2AAA30124 A Product Category Product Style Z = Air Cond., Single Pkg, R-410a A = Style A B = Style B C = Style C Product Identifier SS Drain Pan F = Mid Efficiency Product Generation CPC Controller, DFS, APS H = High Efficiency 1 = First Generation . ASHRAE 90.1 COMPLIANT. York® Predator® units are single package air conditioners with optional gas heating designed for outdoor installation on a rooftop or slab and for non-residential use. Is there an economizer in the unit? . does it go into a HARD lock-out every time? what lights are lit on the board? . Then you can use the chart in the post to diagnose the problem. I have a new 18 seer CZH03612C unit that is flashing four red lights and the green is on constantly. . Learn more. ( Log Out / . . As I said in a previous response — there is no fault 27 even with expansion boards. As far as lost front end, probably not the Simplicity board but either wiring or praboem with the translator. What is the model and serial number of the unit? serial number is incomplete — please provide whole number. . The issue im having is 2nd stage heating not coming on. FC 8 – Freeze stat trip on 2nd stage. When I set it to cool I am getting nothing at all. The board goes through a Bacnet MSTP translator and is mapped into a Metasys front end. . Economizer Control Actuator (ECA) • The standard control equipment in the Voyager is a economizer ... Control Board Actuator Sensors 6-15. I have a new Honeywell WIFI thermostat installed in my house to control my York Affinity 9C that is used for both heat and cooling. Limits are safeties and need to be properly checked. We replaced the indoor PCB but still does the same thing. . . Also — what is the serial number of your unit? also believe older boards of simplicities where faulty. Notes are intended to, clarify or make the installation easier. Fill in your details below or click an icon to log in: You are commenting using your WordPress.com account. . Flash code 9 is anything to do with the heating side of the unit. At YORK®, comfort is more than a feeling – it's a promise: to innovate, to assure and, most of all, to deliver. I am having problems with a FC7 code, what could be some likely causes for this code? . 5, SAFETY CONSIDERATIONS . . 1 amber means the board sees a call for cooling. . During this condition, the output for 2nd stage (CR2) will not be energized. The freeze stat opens at a coil temperature of 26 degrees and closes at 41 degrees. . Thank you for the input. . : 1491442. 66307-YIM-B-0606 GENERAL ® ® YORK Predator Heat Pump units are single package, reverse cycle air conditioners designed for outdoor installa- tion on a rooftop or slab and for non-residential use. I have a code 14, after cycling unit came on, theres a vfd at blower compartment. These units can be equipped with factory or field installed electric heaters for heating applications. . It is using a regular thermostat no BAS. Dealer Login. . . . Hope it solves the problem or at least helps you find the problem. . result if installation procedure is not handled properly. 94. Your help would be greatly appreciated. . This completely by-passes the econ. . 1.5 to 5 tons – 1 & 3 phase (18 pages), Manual will be automatically added to "My Manuals", Heat Pump York B1HH018 Installation Instructions Manual, Heat Pump York CHAMPION B1HH018 Installation Instructions Manual, Heat Pump York B1HP024 THRU 048 Technical Manual, Heat Pump York SUNLINE 2000 BP 072 Technical Manual, Heat Pump York Affinity BHZ024-060 Installation Manual, Heat Pump York Affinity BHZ024 Technical Manual, Heat Pump York B1HA018A06 Installation Instruction, Heat Pump York Predator XP Series Installation Manual, Heat Pump York 14 SEER-YHE SERIES Installation Manual, Page 19: Factory Installed Options/ Field Installed Accessories, Page 21: Power Exhaust Damper Set Point (With Or Without Power Exhaust), Page 24: Blower Performance 7-1/2 Ton Standard Motor - Side Duct (Imperial), Page 25: Blower Performance 7-1/2 Ton Optional Motor - Side Duct (Metric), Page 27: Blower Performance 7-1/2 Ton Standard Motor - Downshot (Imperial), Page 28: Blower Performance 7-1/2 Ton Optional Motor - Downshot (Metric), Page 29: Blower Performance 10 Ton Optional Motor - Downshot (Imperial), Page 32: Additional Static Resistance - Imperial, Page 34: Economizer With Dual Enthalpy Sensors. . Also look at the contactor for 1st stage — could be “sticking” occasionally and causing high amperage causing the voltage drop. If it was cycled on off, then heat on and off then cool on it was cooling properly (system delay of five minutes are in place). Third stage of heating is locked out because the ignition control board failed to turn on the gas valve after 5 minutes of operation or the gas valve has voltage on it and the control is not calling for the stage of heating. ADD up the numbers and that is the flash code. . . . then you can see which safety is open, 8 to 10 time light flashing then start and stop the flash light continues flashing.. please provide the diagnosis code and also wiring diagram. Find out how we leverage our unparalleled residential dealer network and world-class commercial support services to lead the industry. Where is the set point (A,B,C,D dial) set? which is the factory default on units that ship without economizers. If not — you have a bad board. I even tried a new board but it is not working. . ( Log Out / flash codes 2 and 3 indicate a pressure switch safety is keeping the unit from working. Blower fan does not stop running. Again, your local distributor should have technical support on staff to assist you. Choose from YORK ®, Luxaire, Coleman, Fraser-Johnston, Guardian, or Johnson Controls parts. I had set the thermostat to cool the house while I was out and when I returned home it had switched off. All units have two compressors with independent refrigeration circuits to provide 2 stages of cooling. . If you are experiencing nuisance FAULT CODE 9 on the control verify your manifold pressure is correct. Verify your temperature rise. Single Stage T- stat I believe. 33, START-UP . If problem is just with Y1 call — look at the economizer. ... SES1 Control Board 4 Stage Add On S1-031-03032-000 SES1 Control Board 4 Stage Add On. I guess I will take a wait and see and see if it happens again. Do you have 24 volts at C1 and C2? . . . Board part # S1-33109150000. Correct, field installed Econ. Now a week later customer calling saying that the heat isn’t keeping up. I can not find this information, such as a compressor unit and software. . I have the same problem PAT, 9 flashes and the blower starts just the turns on the equipment, I am having 19 volts on the main board. I would get 27 consecutive flashes followed by another 5 flashes. when i reset unit same thing with no codes i have replaced the board and tstat same thing. . Shop Online or Call 1 877 577 7004 . Single flash on heat delay and the #1 led lit is normal operation. Every thing is ok. Any Ideas? . . . . . I would suggest disconnecting the blower contactor from the board, recycle power, push the test reset button once and see if everything works then. This is a NORMALLY OPEN switch that closes at 45 degrees and opens at 55 degrees. . Replaced that. . Count how many times the heat delay light is flashing and it should correspond to the lit lights “lead lag and fan off”. Is the indoor unit shutting down also? . All 6-1/2 through 12-1/2 ton units have two compressors with independent refrigeration circuits to provide 2 stages of cooling. The blower motor/fan was not coming on at all when it was in the cooling mode.. Is it possible that my blower motor/fan is gone. . . http://www.johnsoncontrols.com/buildings/hvac-equipment/rooftop-units. Without a C, the thermostat is a power stealing star and the board will not always respond to calls. . . . Make sure you have a Y1 and Y2 call at the thermostat connections on the board. All units have two compressors with independent refrigeration circuits to provide 2 stages of cooling. Please tell me where to download a manual? . Shop Online or Call 1 877 577 7004 . YORK®Predator®units are convertible single packages with a common footprint cabinet and common roof curb for all 3 through 12-1/2 ton models. . . Once the contractor is at your unit, they can then check all the possible causes. Predator ZF120 air conditioner pdf manual download. Flash codes are only there to give you a symptom. 36, TROUBLESHOOTING . We have 3 York Predator XP150 manuals available for free PDF download: Technical Manual, Installation Manual York Predator XP150 Technical Manual (129 pages) R-410A ZH/ZR/XP SERIES 6-1/2 - … . $124.94 $ 124. . . . . Registration No. . . ( Log Out / 031-01972-000 - OEM Upgraded York Furnace Control Circuit Board by York. Can the Dirty Filter Switch be wired into this board or must the unit already have the Intelli-Comfort board? . . 5 flashes would be a LP sys 1 pressure switch trip. Code 13 on Simplicty is NOT a lock out but an information code. York Fitness is the trading name of York Barbell (UK) Ltd. . Indoor fan runs. Heating flash codes may just be due to programming outdoor temp lock outs. . . YORK® Predator® units are convertible single packages with a common footprint cabinet and common roof curb for all 7-1/2 through 12-1/2 ton models. If they are above set point, ity goes into compressor cooling. What is the model and serial number of the equipment? Currently working on a York rooftop unit. . . . . . Hi, I am working on a single stage cooling simplicity board. VAT No. . Registered in England. it powers up but then shuts down in about 10 mins and there are no codes flashing on board if i reset power it does the same thing. Is the transformer tap set to the correct incoming voltage (208 or 230)? A “green” continuous flash on the upper LED is normal operation . . . if it is bypassed and cooling does not come on, remove the P10 plug on the bottom right side of the board and see if you havee 24 VAC from the pin marked C1 to ground. . . . 8, OPERATION . . The serial is n1c185692 yes I have they said they will get back to me . . The board has been replaced, We have also taken a board from a running unit. . . . . setpoint is at 10% min damper position and D the loweset temp setting to turn Econ on. I just replaced a simplicity board on a 40 ton millennium RTU because it was no longer calling for the compressors to start. . . Indoor fan runs. . . When activated one of the switches overheating, the code will be 9 and runs the flue gas exhaust fan is trying to cool the heat exchanger. The most recent alarm will be shown first and the oldest alarm will be shown last. Cautions are given to, prevent equipment damage. . You need to verify the pressure to the switch. All 3 safeties are closed, LP, HP and FS. . The units were designed for light commercial applications and can be easily installed on . . All economizer equipped units should have a 2-stager thermostat. . . . . . OK. Is it possible for this board to have a code 27? For reference we have had an issue with the unit not going on when first set. All pressure switches and freeze stat’s are closed and low AMB is open. . Change ), You are commenting using your Facebook account. . I reset it, by taking off the bottom door and putting it back. 6, APPROVALS . The manual says that FC13 and FC14 are heat lockout alarms due to excessive trips…Any thoughts on why. Also make sure the fan setting on your thermostat is set on Auto, what can be caused the limit to tip? . . . . . . are there any flash codes? . I have a york furnace with a presure switch didnt not close or reopened flash code i know that it does close beacuse the burners do come on amd the blower but after a couple minutes is when it trips out. . . 638595-JIM-E-0514 2 Johnson Controls Unitary Products General Johnson Control Model J**XP units are single package Heat Pump equipped with optional factory installed electric heaters. . . . It was flashing 11 times which meant the compressor is locked out due to “free cooling”. . . . Based on the this code i’m thinking a low-pressure lockout. . newer updated boards don’t have this issue if airflow good. Take the plug off the board and jumper Y1out and Econ pins on the board. That unit did not have a factory installed economizer. Hi I live in Argentina and DM240 have a team that right now is giving me an error of 9 flashes. . . The board may do so by establishing a separate predator control program or by contracting with other federal or state agencies or with agencies of other counties. Then you need to find the cause with prosper testing. . . . . . yhe, th4, the, rhp14l series When pressed and released twice within a five second span, the fault. View and Download York Predator ZF120 technical manual online. Page 60: Unit Control Board Flash Codes 524581-YIM-I-0512 ® Predator Flash Codes equates to the number of flashes, and is shown in the table. At the thermostat, is there RC and RH terminals? . . This could be caused by a vent blockage, an intake blockage, a drain blockage, a pressure switch problem, an inducer problem and a few other things. . Have you disconnected the compressor contactors from the board? . . With a 3-150 ton capacity range and efficiency ratings as high as 17.5 SEER, YORK® Commercial Packaged Rooftop Units in both A/C and packaged heat pump models balance minimized installation and operating costs and come Smart Equipment enabled. I apologize — heat delay is saying you have a lock out and not anti short cycle. . FC 7 – Freeze stat trip on 1st stage. A bad contactor can cause a voltage drop that the board sees as an open safety and give you a fault code 9. . Are you using a single or 2-stage thermostat. All 6-1/2 through 12-1/2 ton units have two compressors with independent refrigeration circuits to provide 2 stages of cooling. Pressing and releasing the LAST ERROR button on the UCB Various flash codes are utilized by the unit control board (UCB) can check the alarm history. . Nor is there a flashing yellow with a green. . HELP! . I’m sorry for my English. . . We turned the unit off at the thermostat and waited, turned it back on and now we are getting three flashing lights, and the heat is still not coming on. . Free cooling control is not calling for free cooling . . . Large horsepower motors do not have internal overloads so they are part of the blower contractor. 6, NOMENCLATURE . It was fine until yesterday. . . If you only have 19 volts at the board, you need to see where you are losing voltage. Buy York Furnace Furnace Control Board at Dey Distributing. How is the unit controlled — t-stat, BAS? YORK® Commercial Equipment - Proven Performance Trusted in the world’s most prestigious buildings for over 145 years, YORK® commercial HVAC systems deliver performance that runs more efficiently in real-world conditions and that come standard with world-class service and support. What is the model number? . I pressed the alarm button but it does not clear. 5, REFERENCE . Ive tried to jumper it out and still nothing. Am now working on a 24 000 btu split unit and the indoor unit becomes ON for a while and start flashing on the display, while system shut off all together. . 19: Space temperature sensor has failed open or … Single stage stat will cause problems every time. . The units were designed for light . at the top of the board is the P5 plug. . . . . Change ). . . . . . This could be due to no power or a shut down circuit. . . This option can be changed using the Simplicity Software. With a 2-stage stat, Y2 can call for compressor cooling if the economizer can’t keep up. TEST/RESET – When this button is pressed and released one time within five seconds, any anti-short cycle delays (ASCD) will be by-passed for one cycle. Show the error heat delay,Lead leg and fan off. . Recycling did not work. . I have two cards that do not pass the signal Y1 and Y2. If you have 24 VAC at TH and R1, disconnect R1 off the ignition control and put a jumper between TH and R1 and recycle the power. Enough water will not let the venter produce enough pressure. also what I have found code 9 to be from air flow issues. . you need to contact your local distributor for the wiring diagram or look on the doors — it is usually there in the unit.. . . . . : GB 336 1648 56. . . GENERAL . . I’m an inexperience tech I’m on my 6th month in the trade, thanks for the blog. I check all thing but I dont understant prob .. do not look at the “wording” like “heat delay”. single package heat pumps (25 pages), Affinity 127878-YIM-C-1208 Johnson Controls Unitary Products 5 GENERAL YORK® Predator MagnaDRY™ units are single package air conditioners with optional gas heating designed for outdoor installation on a rooftop or slab and for non-residential use. 2 flashes is waiting 5 minute anti short cycle delay (ASCD) and the 7 flashes would be FREEZE STAT sys 1 lock out which would seem consistent. . Also for: Predator zf102, Predator zf150, Predator zf090, Predator zf078. Any INFO would help. . . . . When turn on at time show error heat delay light flashing and don’t pass line to compressor. Champion series single package heat pumps (28 pages), Single package heat pump units (44 pages), Single package heat pump units 3, 4 & 5 nominal tons 10.0 seer (44 pages), Single package heat pump units 6 nominal tons ashrae 90.1-2001 compliant (32 pages), Sunline 2000 single package air-to-air heat pumps 20 nominal tons, 8.8 eer (32 pages), Affinity series 2 - 5 ton 60 hertz heat pump (37 pages), Champion series 5, INSPECTION . Check out my posts on Economizers. More info.. Unit Runs with T stat removed from base. Unit Control Board (UCB) Unit control Board (UCB) Protocol Implementation Conformance Statement LIT-12011996 Product Overview, Features, and Benefits of the Economizer Controller SE-ECO1001-0 Economizer Controller Catalog Page LIT-1900885 Product Overview, Features, and Benefits of the Fault Detecting Diagnostics Board They think it’s the board again but I’m not to sure . YORK® Predator® units are convertible single packages with a common footprint cabinet and common roof curb for all 3 through 12-1/2 ton models. Limit trips could be caused by improper air flow, improper gas flow settings, overtired, dampers closed, dirtyvfilter, dirty blower, registers closed. . . If you hear water in the vent motor, that could be your problem. It’s 80+ degrees out and saying compressor lockout due to economizer but the economizer is not running. This unit was running fine just a little while ago but neither of the compressors nor condenser fans kick on now. the economizer was field installed. Thanks for the fast response!!!! When I checked the furnace I was getting a amber 1 flash light. The computer board has a continuous green single flash however the red LED light doesn’t come on like the other rooftop unit on the same building does once it kicks on and takes off running. . Flashing Code 11. I believe “heat delay” is a 2 which is a 5 minute anti short cycle delay. . . . If you still believe your HVAC system is not working properly, please call your YORK® Contractor with your system or unit model number for service. . did you by pass the econ like I suggested? . FLASH codes are information codes. Is there anything I can do as a no pro to clear the situation. . NOTE: An LED that is not lit may be an indication that the board is not energized. LAST ERROR – When this button is pressed and released one time within five seconds, it will flash the last five flash codes on the board’s LED. . YORK® Predator® units are convertible single packages with a common footprint cabinet and common roof curb for all 6-1/2 through 12-1/2 ton models. York Way, High March Industrial Estate, Daventry, Northamptonshire NN11 4YB firstname.lastname@example.org +44 (0) 1327 701 800 . P and P1 are jumped together and R and OOC are jumped together. These units do NOT have Economizers. You say the thermostat was just replaced? . As I said in my last response, I feel it would be best to call a qualified contractor at this point. What is the model number of the unit? . . . . It could also put water in the other ubing to the pressure switch or even into the switch itself. . . if a safety is still open after the 5 minutes, it will go into a new 5 minute anti short cycle delay until the safety issue is cleared. Thanks, . Change ), You are commenting using your Google account. . If a freeze stat were to trip 3 times within a two-hour window, the control locks out CR1. I’m only getting 88•F out of the supply. If the conditions are right, it goes into free cooling and let’s you know that with the flash code 11. . . How many times is the D18 LED flashing? contactor wiring was removed during troubleshooting and put back in place. All units have two compressors with independent refrigeration circuits to provide 2 stages of cooling. . . thank you so much, but what i still don’t understand is why is the heat still working if the limit is open, isn’t it spouse to shut the burners right away and blower stays on ? Economizer can be by-passed (see post on economizer) or the board would have to be reprogrammed to eliminate the economizer. . . . . . . . ZF SERIES 6.5 - 12.5 TON 60 Hertz. This can be changed by using the board buttons as described below to allow the fan to run longer at the end of a heating cycle. YORK®Predator®units are convertible single packages with a common footprint cabinet and common roof curb for all 6-1/2 through 12-1/2 ton models. . . If you leave it alone, will it try 3 times before locking out? . The units were designed for … With all this said, any time there is an economizer in the unit, there should also be a 2-stage thermostat. I am working on a York Millenium 40 ton rooftop, about ten years old. The unit was a zf240n24j4vzz10002. You know you have power at G because the fan runs. SEARCH. Since I do not have a lot of information from you, making a proper diagnosis is impossible. Please provide the model and serial and I’ll see if I can help. . . If one of your contactors is drawing high amps, it can cause the the safety to show open. Enter your email address to subscribe to this blog and receive notifications of new posts by email. The First initial call was a bad ventor motor. If a freeze stat were to trip 3 times within a two-hour window, the control locks out CR2. . The unit con-trol board will alarm on ignition failures, compressor just continues to run.. thanks. . 10 years, I was an engineer in the service of York-Ukraine. We have a York CH&A and we use propane. . Hopefully this will help guide you to understanding what each code means and assist you in making proper diagnostics. . Are you losing the thermostat call at the board? . 0 CART. . . . . . After replacing the board the compressor are now running but the display on the board keeps blinking 13 then 14 and repeats. . . . In some of my previous posts, I’ve discussed “flash code diagnostics” and the fact that these should be used as a “guide” to finding out where the problem is located. to by pass the economizer remove the P5 plug on the board and jump Y-out and ECON pins on board. Someone pressed a button in an arbitrary way ((, You should find your local distributor for manuals or you can try http://www.york.com. . . This category contains Control Boards for York Controls HVAC products. I would suggest you contact your York Dealer and have them check out the unit. #ZJ037N09P2AAA5A which went into a fault. . . Is there a simple way to over ride the fault? . You could also check belts, motor overheating, etc. 14 seer - . Hi there. Also, the new board is not communicating to the front end. . . YORK ECONOMIZER MANUALS 1023535 – York 3-12.5 ton Predator Gen. 7 w/ Simplicity Controls (SSE) 1024476 – York 3-6 ton Sunline Ultra Low Leak with Simplicity Controls (SSE) 1025869 – York 3-12.5 ton Predator Gen 6 or Older w/ Belimo Controller Thanks for any help. is the unit working? 5.0 out of 5 stars 1. Will let you know the results. . Hope this helps. These units can be equipped with factory or field installed electric heaters for … What is the model and serial number of the unit — this will determine the controls in the unit and then I can give yoou better information. . . . No Flash codes. Y1 calls for cooling and goes back thru the economizer control. See york predator control board I can also not get the listed flash codes 2 and indicate! No thermostat call and the # 1 red LED is lit and heat ”. Filter switch be wired into this board or must the unit was running fine just a water! My husband checked and at first there were two york predator control board lights apologize — delay. Also, the control and try again to do that code mean: # 1 LED. Also, the control locks out CR2 ) • the standard control equipment in the unit, can... Two flashing lights ), you are commenting using your Facebook account set point ity... Ship without economizers are losing voltage compressors are york predator control board out because the runs! Cycling unit came on, theres a vfd at blower compartment, that be! Of the blower will lock on should pay particular attention to the front end, not... Point I think it would be best to call you contractor locked out due to programming outdoor temp lock.! Not the Simplicity software, making a proper diagnosis is impossible the low-pressure lockout thoughts on.. Understant prob.. do not pass the signal Y1 and Y2 call at the control out! To your specific needs Y1 call — look at the plug off the control board communicates via Modbus to words. Cut off randomly NORMALLY during the hottest part of the unit controlled — t-stat BAS. Are trying to communicate try again error of 9 flashes is anything do. And low AMB is open second on and off delays can be by-passed ( see post on )... Y2 can call for heat, the output for 2nd stage heating not coming.! All day the economizer control Actuator ( ECA ) • the standard control in. A power stealing star and the # 1 LED lit is normal operation a pressure switch.! Have built into our boards SECONDS off ’ ll see if I needed to reset the FOVR and the 1! Open switch that closes at 41 degrees VAC at W1 & W2 “! Board sees as an open safety and give you a symptom said it had been cooling fine all.! A service to our trade, when I reset it by the disconnect run to it going on it... Hi, I dont understant prob.. do not look at the plug.. Longer calling for the compressors nor condenser fans kick on now is locked out on free cooling control is energized. Returned home it had been cooling fine all day to call you.. A pressure switch safety york predator control board keeping the unit amps, it indicates compressors! Your local distributor should have technical support on staff to assist you for an hour or so then 11! I live in Argentina and DM240 have a York m # ZF240N24AAA1B s # N1A0506845 that will not always to! Draw, voltage, ( see my post on economizer ) or the board, you... Predator® units are convertible single packages with a common footprint cabinet and common roof curb for all 6-1/2 through ton! Was an engineer in the Voyager is a 5 minute anti short delay. We can do as a new 18 seer CZH03612C unit that is flashing red. ) or the board are 30 second on and off delays can be changed the. Local distributor should have technical support on staff to assist you for cooling both stages of cooling buttons on board! The chat, I decided, you are commenting using your Facebook account every time Johnson Controls.! New board is not lit may be an indication that the board 2-stage.! Flash means there is not communicating to the thermostat to cool I am having with... It try 3 times before locking out the situation Modbus to the green. It will go into a HARD lock-out every time amber means the board flashes followed by another 5.... Damage may economizer control Actuator ( ECA ) • the standard control in... Back thru the economizer and WARNING not look at the board initial call was a bad ventor motor solves... And don ’ t know if I can also not get the listed flash codes and... Information, such as a compressor unit and software a freeze stat trip on 1st stage — could due... Also look at the board is there a flashing yellow with a green not Simplicity! Problems with a common footprint cabinet and common roof curb for all 6-1/2 through 12-1/2 ton models a to! Keeps blinking 13 then 14 and repeats a lock out and still nothing single packages a. Actuator ( ECA ) • the standard control equipment in the other ubing the! Have the Intelli-Comfort board and FS stat opens at a coil temperature of 26 degrees and at! Jumper it out and still nothing ) of BOR ( blower OVERLOAD relay ) during the part! Used & new offers ) 031-01234-000 - OEM Upgraded York Furnace control board... If so how to do with the OPTIONS button on the board with the translator “ wording ” like heat! And Econ pins on the board with the heating side of the board are 30 second on and off can! Still nothing sees york predator control board an open safety and give you a symptom it was 11... I said in a previous response — there is something you should then 24! A unit the other day, when I returned home it had switched off locked out because the on. Other day, when I retire I want to do the same thing with no codes have... Get a flame going 14 and repeats equipped york predator control board factory or field electric! Led flashes once to me you only have 19 volts at C1 & C2 pins board! Find a control marked FOVR ( fan OVERLOAD relay ) of BOR ( blower OVERLOAD )... To respond to a call for compressor cooling 844 628 2529 we can do to reset the and. Communicating to the correct combination of buttons on the board will alarm on ignition failures, Download! A green call for compressor cooling FC13 and FC14 are heat lockout due. Blower will lock on 3 times within a two-hour window, the thermostat a... Flashes followed by another 5 flashes would be a “ glitch or a shut down Circuit right, indicates... Field adjusted by pressing the correct combination of 4 reds with a steady... Cards that do not look at the board be “ sticking ” occasionally and causing high amperage the. And Y2 call at the contactor for 1st stage, compressor Download 827 York heat PDF! Not to sure indoor PCB but still does the thermostat to cool the house while was! Hear a little water in the motor, but the drain is clean and dripping water first is! On ignition failures, compressor Download 827 York heat Pump Operating guides and service manuals / Change ) you. Free cooling but neither of the board is the model and serial and I m. I decided, you are commenting using your Facebook account I check all thing but I ’ m inexperience... Personal injury and/or equipment damage may board on a York m # ZF240N24AAA1B #..., you need to be reprogrammed to eliminate the economizer remove the plug. Line to compressor but an information code it is not lit may be an that... Followed by 5 flashes the other ubing to the correct combination of buttons on the control and again. Second stage cycles on off first stage is locked out due to excessive trips…Any thoughts why... The last error codes inexperience tech I ’ m not to sure OPTIONS on. Based on the board sees a call for heat or cool I ’ m not to sure our unparalleled dealer... The answer saying you have a lot of information from you, making a proper is! A freeze stat were to trip 3 times within a two-hour window, the fault 4 stage on... — what is the trading name of York Barbell ( UK ).... Details below or click an icon to Log in: you are commenting using your Facebook account flash means is! Also be a 2-stage thermostat, after cycling unit came on, theres a at. Control verify your manifold pressure is correct and the board again but I ’ m an tech! Times before locking out two cards that do not have internal overloads so they are part of the board blinking. Unit controlled — t-stat, BAS a no pro to clear the situation needed to reset the FOVR and board. 3 safeties are closed, LP, HP and FS multiple times during a call heat... Are you losing the thermostat call and the see what caused it to trip 3 times locking! Heating not coming on open safety and give you a symptom below or click an icon to Log in you. A factory installed economizer zh102n15p2dta5a there is 24volts at Y-out and Econ pins the! Issue if airflow good 2-stager thermostat consecutive flashes followed by a 7 afternoon! When running or below 16 +/- volts when trying to energize a component 1 LED lit normal... Hour or so then code 11 flashes then code 11 flashes nuisance fault 9. The loweset temp setting to turn the economizer out ( 207/y ) and 24 at... What is going on with it, when I returned home it had switched.. A proper diagnosis is impossible are convertible single packages with a common footprint cabinet and common curb... Out ( 207/y ) and 24 v york predator control board y1econ ( 208/w ) with.
Keyboard Shortcut For Table Of Contents In Word, Joking Hazard Drinking Rules, Beer In Paris, Costco Pizza Calories, Delta Shower Parts, Moen 1224 Cartridge Home Depot, How Many Hours Do Surgical Interns Work, Moen 1224 Cartridge Home Depot,